This Practice provides requirements for design and manufacture of horizontal centrifugal pumps of 150 kW (200 HP) or greater used for general water services.
Comment: General water services include condensate, cooling water, demineralized water, utility water, produced water, treated water, etc.
This Practice covers pumps with service conditions within the following limits:
a. Maximum discharge pressure 35 Barg (500 psig)
b. Minimum pumping temperature 0°C (32°F)
c. Maximum pumping temperature 150°C (300°F)
d. Maximum rotational speed 3,600 rpm
Comment: For services within the capabilities of ANSI/ASME pumps, use PIP RESP73H.
Pump types covered by this Practice are broadly classified as overhung or between-bearings. The following pump types are not included in the scope of this Practice:
a. Close coupled (i.e., impeller mounted on the motor shaft)
b. Two-stage overhung
c. Double suction overhung
Fire water pumps are covered by NFPA 20 and are not covered by this Practice.
- Number of Pages:
- File Size:
- 1 file , 620 KB